An electrical heater plate is used to raise the temperature of the pipe ends to the required fusion temperature. Butt-fusion can be used to join both PE80 and PE100 materials for pipe sizes of 90mm and above of the same SDR.
The butt welding machines used to weld PE pipes have controls to ensure the welding parameters are strictly adhered to. The following parameters are controlled:
*heater plate temperature
*ovality and alignment
*heat soak time
Control of these is necessary to ensure premature failure of the weld does not occur. The field conditions under which PE pipe is welded have a considerable effect on the strength of the joint. In order to achieve an acceptable weld three elements are essential:
*Cleanliness: because contamination will ruin joints
*Technique: Most owners of PE pipe systems require that people performing butt welding of PE pipes are qualified by completing a recognised training course
*Correctly designed equipment with proper maintenance: Correct welding temperatures, welding procedures and pipe facing tools must be maintained in tolerance and in good condition.
The resulting joint, if it has been properly made, is as strong as the original pipe and can withstand all the loads applied during routine installation and operation.
During the fusion process internal and external ‘weld beads' are formed. Techniques have been developed to minimise the size of the beads, however as they do not add anything to the overall strength they may be safely removed if required. The removed weld beads can be inspected as part of a quality control programme.